A.Facilities with six (6) or more licensed beds shall have a partial, manual, automatic, supervised fire
alarm system. The facility shall arrange the system to transmit an alarm automatically to a third party. The
alarm system shall notify by audible and visual alarm all areas and floors of the building. The alarm system
shall shut down central recirculation systems and outside air units that serve the area(s) of alarm origination
as a minimum.
B.All fire, smoke, heat, sprinkler flow, and manual fire alarm devices must be connected to and
activate the main fire alarm system when activated.